|Place of Origin:||China|
|Minimum Order Quantity:||10|
|Delivery Time:||10-15 days|
|Payment Terms:||L/C, T/T, Western Union,Paypal|
|Supply Ability:||5000 pieces per month|
|Material:||Cast Aluminum||Type:||Junction Box|
|Application:||Hazardous Location||Product Name:||Explosion Proof Terminal Box|
|Ex Marking:||Exe II T6 Gb, Ex TD A21 IP65||Outlets:||Custom|
In order to protect signal and power distribution networks from harsh environmental conditions and explosion hazards, various types of flameproof terminal boxes and junction boxes are available.
Several enclosure variants and material options as well as customized configuration with terminal and cable gland types allow adaption to any application requirements.
Suitable ingress protection and ambient temperature ranges as well as rugged enclosure materials such as copper-free aluminum, stainless steel, and cast iron ensure long-term durability and safe operation
|Execution standards||GB3836.1, GB3836.2, GB3836.3, GB12476.1, IEC60079|
|Rated voltage||AC 380V/220V/110V/36V/24V|
|Explosion-proof mark||ExeII T6 ExtD A21|
|Introduction port specification||G1/2"~G2.5"|
1. Can be used in hazardous areas: Zone 1 and Zone 2 .
2. Can be used in explosive gas atmospheres of Category IIA and II B IIC where the temperature classification is T6.
3. Two type of Ex d(IIB) and complex(IIC).
4. Flammable dust atmosphere.
5. Widely using in the fields of oil, chemical industry , spaceflight ,war industry and so on
When installing, open the junction box cover and the introduction device, select the appropriate inner diameter of the sealing ring according to the outer diameter of the cable, and then pass the cable through the compression nut of the introduction device, the gasket and the sealing ring are connected to the cavity, and fasten. The compression nut seals the cable, the introduction device that does not introduce the cable replaces the cable with a plug, and tightens the compression nut. Connect the wire to the corresponding position of the terminal block, connect the grounding wire, close the cover, and fasten the cover with bolt.